Single Phase Chiller Controller
1.Under normal working condition at power on after delay of 1 min.FAN1 will Start (ON),after 2 mins.FAN2 Starts(ON),after 3 min delay Compressor will Starts(ON).
2.While compressor is ON,if HP,LP,OL occurs then Compressor and FAN2 will be Shut Down(OFF).
3.IF UV /OV occurs then Both FANs and compressor will be Shut Down(OFF).
Supply Voltage: 230 VAC ± 15 %.
Output Contact Rating:
30A,250V for Compressor.
7Amps,at 250 VAC for FAN1/FAN2.
1) 3 seven Segment bright LED Display
2) 3 Keys for settings.
3) Fault indication by Red LED.
4) Compressor, FAN1/2 Green LED.
1) Temperature, Antifreeze Temp. HP, LP
2) Current & Voltage sensing.